"One equipment control building designed to be blast resistant and two each of three standardized types of metal warehouse or utility buildings were exposed to the effects of a nuclear device detonation. One of the utility buildings was frameless, with deeply corrugated wall and roof sections; a second was very largely frameless, utilizing interlocking channel sections; and in the third the aluminum-panel wall and roof covering was supported by girts and purlins, which in turn were supported by steel frames. Because of atmospheric conditions at the time of an earlier detonation in the test series, one of each of the three types of utility buildings was exposed to approximately 0.7 psi overpressure before the planned test. In the planned test, held during the open shot (Apple II), one of each of the three types was exposed to approximately 3.0 psi overpressure and one to 1.3 psi, with the intention of bracketing their overpressure survival range and obtaining data for possible economic redesign for Improved blast resistance. The equipment control building utilized continuous-welded steel frames and reinforced-gypsum curtain-wall construction. The control building was exposed to approximately 4.1 psi, in the anticipated fringe zone of major structural damage, to determine its protective capabilities."
United States. Department of Energy. Office of Scientific and Technical Information: http://www.osti.gov/